Dear Barry: When I purchased my home, I hired a home inspector. The only electrical problem he found was a charred wire in the fuse box. After moving in, I noticed that the lights kept dimming, so I called an electrician. He said that the panel was very old, that the charred wire was actually burnt through, and that some of the fuses were connected to more than one circuit, a condition he called “double-tapping.” Now I need to install a new breaker panel for a whole lot of money. So I called the home inspector. He said that he does not take things apart and inspect the inner workings. If that’s so, then how did he see the charred wire? What do you think I should do? Ryan
Dear Ryan: The home inspector is apparently giving you double-talk. It is the standard of practice for home inspectors to remove the inside cover on every electrical panel to enable inspection of the internal components. As you pointed out, your inspector apparently did this, or he would not have disclosed the charred wire. Therefore, he was in a position to see the other electrical defects and should have disclosed them. Even if he only disclosed the charred wire, his recommendation should have been evaluation and repair by a licensed electrician, prior to close of escrow, especially since this was an outdated fuse panel, rather than a breaker panel. Had he given you that advice, the remaining defects could have been discovered by the electrician before you took possession of the property. If he did not provide full disclosure of the panel defects and did not make the proper recommendation for the charred wire, then he should take some responsibility for lack of disclosure
On the other hand, if he did disclose further evaluation by a licensed electrician, it would have been your responsibility to follow that recommendation. In that case, failure to have followed the inspector’s advice would place the liability back in your court
If by these standards the home inspector remains liable, be sure to take photos of the electrical defects before having them repaired. This will enable you to prove your cased if you file a claim against the inspector
Dear Barry: We bought our home about 6 months ago, and now we are stuck with a bundle of problems that were concealed by the sellers, dismissed by the agent, and overlooked by our home inspector. Unfortunately, our agent was also the listing agent for the sellers, who happen to be her personal friends, and she also selected the person who did our home inspection. The main problem with the house is ground water seepage into the basement. The seller disclosed that there used to be a drainage problem that was corrected, but they provided no documentary proof of the alleged repairs. When we first looked at the property, we noticed a musty smell and pointed this out to the agent. She said, “I’ve been an agent for a long time. This just smells like an old basement, not a moldy one, and I know the difference….” She also persuaded us to buy the property “as-is” so that the sellers would accept our offer. After moving in, we discovered that the basement carpet was wet. When we removed it, we found mold and rot on the baseboards. We have also learned that the sellers hired a contractor to dry out the carpet and repaint the basement before we bought it. The costs to correct the drainage, repair the water damage, and eliminate the mold are very high. What can we do? Patrick
Dear Patrick: If you had written to me during the course of the transaction and said, “Dear Barry, We are buying a home that has musty odors, the dual agent (who is a friend of the sellers) says this is not a problem, the agent has chosen our home inspector, and the agent is persuading us to buy the home as-is,” I would have told you the following: “The agent is representing the interests of the sellers only. You need someone to represent you, which means find an agent of your own to help you negotiate.” I would also have advised you to hire your own home inspector, not an inspector who was chosen by an agent with an apparent bias.
Agents know which home inspectors are the most qualified and thorough. An agent who is more interested in the commission check than doing what is right will recommend inspectors who disclose fewer defects. To those agents, the best inspectors are known as “deal killers.”
My advice is two-fold. First, have your home re-inspected by a qualified professional who has many years of experience and a reputation for thoroughness as an inspector. Whether the agent’s home inspector is liable depends on whether there were visible defects that were within the scope of a home inspection, as defined by industry standards. Call several real estate offices and ask who are the most nit-picky inspectors in the area.
Second, get some advice from a real estate attorney regarding your available options for redress against the sellers and the agent for nondisclosure, and against the home inspector for professional negligence. Certified letters on legal stationary should alert all parties that you are very serious about this matter.
The House Detective: by Barry Stone, Certified Building Inspector
Dear Barry: We are buying a brand-new home and were not planning to have a home inspection because the house was just approved by the county building department. Then we read your recent article about inspecting new homes, so we hired a home inspector and got some big surprises. He found two plumbing problems in the crawlspace under the house, three ungrounded outlets in the living room, and a safety violation concerning the furnace in the attic. What I want to know is, how could these defects have been overlooked when the county did their final inspection? Jason
Dear Jason: Whenever I begin to inspect a brand-new home, I wonder if this will be the first one where I find no faulty conditions of any kind. So far, no cigar.
So the question is, how do so many defects escape discovery by municipal inspectors? In most cases, incompetency is not the problem. In your situation, involving undiscovered defects in the crawlspace and attic, as well as three ungrounded outlets, the problem does not necessarily involve ineptitude on the part of the county inspector. More likely, it is due to endemic shortcomings with the municipal building inspection process.
Some municipalities may be exceptions to this, but in general, building inspectors do not crawl under houses or through attics. They are not even equipped with ladders or with crawl suits. This means that faulty conditions in those areas of a house are never subject to the final inspection. As a result, any problems with plumbing, wiring, heating, framing, insulation, etc. in those places are never seen during the final inspection and remain as-is when the construction is signed off by the inspector. That is why further inspection by a qualified home inspector is always a good investment.
As for the ungrounded outlets, here is why those were not discovered by the municipal inspector. The power company does not turn on the electrical service to the property until the final inspection has been officially approved. Therefore, the power is off during the final inspection. Without power, there is no way to determine whether outlets are grounded, whether they have correct polarity, or whether any of the electrical fixtures are actually operative.
Home inspections, on the other hand, take place after the utilities are turned on, and unlike municipal inspectors, home inspectors test the functional condition of fixtures and use test devices to determine whether outlets are properly wired.
The main differences between municipal inspections and home inspections are these: Municipal inspections are for code compliance only, and they are limited locations that are accessible by pedestrian means only. Home inspections involve not only compliance with building standards but with quality of workmanship and with functional and safety-related conditions that are outside the scope of the building code. What’s more, home inspectors go where most municipal inspectors are unlikely to go in an entire career: to places that entail crawling in the dirt or through narrow cavernous recesses.
Municipal inspections should be regarded as a preliminary final inspection. Home inspections, when done by a qualified inspector, should be regarded as a “final” final inspection.
The House Detective: by Barry Stone, Certified Home Inspector
Dear Barry: I purchased my house about a year ago. At the time, the bathtub seemed to be OK, but now it is apparent that it was painted to cover rust. I also found plumbing problems under the sinks, but none of these issues was reported by my home inspector. What can I do about this? Dawn
Dear Dawn: The parties who are potentially liable are the sellers and your home inspector. Sellers are required to disclose all known defects. However, the sellers in your case may not have thought the painted tub was a defect. It might have seemed to them that this was a former defect, having been repaired with paint. Unfortunately, paint is not a permanent repair for the damaged finish on a bathtub. In most cases, chipping or peeling eventually occurs.
Home inspector liability depends on whether the problems were visible at the time of the inspection. The paint on the tub may not have been obvious at the time of the inspection.
As for the plumbing problems, seller liability depends upon whether the previous owners were aware of those issues and whether the problems even existed prior to the sale. Home inspector liability depends on whether the problems were visible and accessible at the time of the inspection. If the problems involve leakage, that may or may not have been occurring at the time. If there are installation defects, they may have been obscured by storage under the sinks, as is often the case during home inspections.
You should contact your home inspector and request a second look at these problems.
The House Detective: by Barry Stone, Certified Home Inspector
Dear Barry: My home was built in 1926 and has asbestos insulation on all the hot water pipes under the building. Fortunately, all of this asbestos has been wrapped. When I first learned about it, I was horrified and wondered why my home inspector hadn’t mention it when I bought the property. My main concern is what will happen when I eventually want to sell the home. Can I resell it in this condition, without penalty? Am I required to have the asbestos removed? And also, do I have recourse from my home inspector for not mentioning the asbestos? Judy
Dear Judy: Asbestos pipe insulation was common in the 1920s and is not regarded as a significant health risk when it is undamaged and intact. Fortunately, the asbestos insulation in your home been encapsulated, rendering it in much safer condition than when it was exposed to the air.
As a seller, there is no requirement for removal of asbestos, and there are no penalties for merely having it. Your only requirement will be to provide full disclosure to prospective buyers, to let them know that the asbestos material is present. If the former owners were the ones who had the pipes wrapped, they probably knew about the asbestos and should have provided some disclosure.
Environmental hazards such as asbestos are not within the scope of a home inspection. However, competent inspectors who take their work seriously will often point out situations where the presence of asbestos is likely, such as insulated pipes in an old home. This is something that your home inspector would have been wise to do, even though not required to do so.